Code Conundrum June 2018 • Ray Yousef
July 27, 2018 — Tackle June 2018's Code Conundrum...if you dare!
In a dwelling unit’s panelboard, what is the maximum mounting height for the overcurrent protection device handle?
a) 1.5 m
b) 1.6 m
c) 1.7 m
d) 1.8 m
Moulded-case circuit breakers are permitted to be located in a Category 2 location so long as they are contained within a NEMA-1 enclosure.
Unless it forms part of a motor-operated device, a portable motor shall be permitted to be connected using flexible cord of a serviceability not less than that of Type S.
Answers to this month's questions in July/August's Electrical Business. MEANTIME, here are the answers to the May 2018 Code Conundrum!
Conductors for equipotential bonding shall be permitted to be installed as open wiring, provided they are adequately secured.
a) True. Rule 10-702(1), CE Code 2018.
Which of the following insulated wires can be marked permanently with a green colour to be used as a bonding wire?
d) #1AWG. Rule 4-032(1), CE Code 2018.
The maximum voltage for a class 2 circuit is:
d) 150 V. Rule 16-200, CE Code 2018.
How did YOU do?
3/3 = Master Electrician
2/3 = Journeyman
1/3 = Apprentice
0/3 = Bricklayer?!?
April 24-25, 2019
Partners in Prevention Health & Safety Conference & Trade Show
April 30-1, 2019
OEL Electrical Industry Conference
May 1-4, 2019