Code conundrum March 2017 • Ray Yousef
March 14, 2017 - Time to brush up on those CE Code skills!
Does the CE Code permit a bare neutral in a consumer service (when the conductor is made of copper and run in a raceway)?
Overload protection shall not be required for a manually started motor rated at ___ hp or less when: it is continuously attended while in operation, and is on a branch circuit having overcurrent protection rated at (or not set at more than) 15A; or on an individual branch circuit having overcurrent protection (as required by Table 29) when it can be readily determined from the starting location the motor is running.
a) 1/2 hp
b) 1 hp
c) 2 hp
d) 5 hp
Plug fuses and fuse holders shall not be used in a 240V single-phase, 3-wire grounded system.
Answers to these questions next month. Meantime, here are the answers to the February 2016 Code Conundrum:
The maximum ampacity for #6 AWG T90 nylon run in a conduit containing 6 #6AWG T90 nylon, 12 #14AWG TWU75 and 7 #12AWG TW75 is:
d) 33A. Rule 4-004(15) and (14).
Electrical equipment suitable for non-hazardous locations may be installed in a ventilated Zone 2 area when it is continuously monitored by a combustible gas detection system that automatically de-energizes the equipment when gas concentration reaches ___ of the lower explosive limit.
d) 40%. Rule 18-068..
Pendant lampholders in Category 1 locations must be weatherproof, unlike Category 2, where corrosive liquids exist.
b) False. Rule 22-104..
HOW DID YOU DO?
• 3/3 = Master Electrician
• 2/3 = Journeyman
• 1/3 = Apprentice
• 0/3 = Plumber?!?
The Code Conundrum is compiled by Ray Yousef of Ontario’s Electrical Safety Authority.
N.B. Always consult your AHJ for more specific interpretations
* This article also appears in the March 2017 edition of Electrical Business Magazine. Check out our ARCHIVE page for back issues.
5th Annual Electric Elle Golf Tournament
September 12, 2017
Become the Obvious Choice in a Competitive Market • WEBINAR 3/4
September 12, 2017
28th Annual Bob Carson Classic Golf Tournament • ECAA
September 13, 2017