February 14, 2017 - Believe it or not, it’s that time of year when firms start looking ahead to the camping season and campground upgrades. Nothing much has changed in recreational vehicle parks over the past CE Code cycle, but a number of changes took place over the past 15 years to make this part of the code clearer.
December 12, 2016 - An interactive power production system operates in conjunction with—and can deliver power to—another power system, such as the utility. While this could involve a standard generator, I will focus on renewable energy systems.
November 9, 2016 - The main purpose behind matching the conductor with the correct overcurrent protection is to safeguard the downstream conductor from overload and/or short circuit. Based on that simple concept, the rating of overcurrent protective devices (OCPD) always needs to be equal to or lower than the ampacity of the protected conductor.
October 11, 2016 - CE Code Section 10 “Grounding and bonding” talks of bonding metallic systems together to the grounding conductor. This reduces the danger of electric shock and property damage by providing a low impedance path for fault current back to the source, and establishes an equipotential plane, such that the possibility of a potential difference between metal parts is minimized.
September 12, 2016 - In 2013 I published a column very similar to this one to raise awareness about the hazards with delta (ungrounded) to wye (grounded) conversions. Delta systems have become increasingly less common—many of the experts on these systems have retired and lessons learned have been forgotten.
August 10, 2016 - The building code defines a vapour barrier as “the elements installed to control the diffusion of water vapour”. Did you notice it says “control” not “eliminate”?
July 7, 2016 - Equipment marking contributes to the safety of electrical installations by identifying switches and breakers so that circuits can be de-energized, allowing for the timely and accurate identification of circuits so that loads are not inadvertently de-energized; and providing workers with the means to de-energize circuits more conveniently, reducing the likelihood that a worker will engage in unsafe work practices.
PowerTest 2017 by NETAMon Feb 27, 2017
AEA Electrical Learning Expo 2017Thu Mar 02, 2017
The Work Truck Show 2017Wed Mar 15, 2017