February 13, 2018 – With the steady increase of electric vehicles on our roads, the 2018 CE Code (publishing this month) includes new Rules that recognize EV energy management systems (EVEMS), which address evolving EV technology and issues associated with future loading on electrical infrastructure.
January 22, 2018 — The number of changes coming to the 2018 CE Code are fairly substantial, and while a number of them involve tweaked wording and/or definitions, there are also a fair number of what I would call “significant” changes.
October 6, 2017 — Rules in Section 16 (New 16-300 series added) of the upcoming CE Code 2018 have been amended to include requirements for Class 2 power and datacom circuits. Although the new requirements do not reference “Power-over-Ethernet” (PoE) terminology, an Appendix B Note is added to explain the “Class 2 power and data communication circuit” is based on the concept known as PoE, introduced by the IEEE 802.3 series of standards.
September 15, 2017 — In addition to a number of changes in 2012, CE Code Section 62 “Fixed electric heating systems” underwent a fairly substantial rewrite in 2015. So what’s changed?
June 28, 2017 - What do circuit loading and demand factors mean, and how are they different? A circuit load is a component or portion of the circuit that consumes power. A demand factor is a time-dependent fractional quantity that will always be less than, or equal to, one. Huh?
May 26, 2017 - Required by the National Building Code (NBC), smoke alarms must be permanently connected to a lighting circuit, or one that supplies both lighting and receptacles, so as to quickly detect when there’s a problem with the circuit.
February 14, 2017 - Believe it or not, it’s that time of year when firms start looking ahead to the camping season and campground upgrades. Nothing much has changed in recreational vehicle parks over the past CE Code cycle, but a number of changes took place over the past 15 years to make this part of the code clearer.
December 12, 2016 - An interactive power production system operates in conjunction with—and can deliver power to—another power system, such as the utility. While this could involve a standard generator, I will focus on renewable energy systems.
November 9, 2016 - The main purpose behind matching the conductor with the correct overcurrent protection is to safeguard the downstream conductor from overload and/or short circuit. Based on that simple concept, the rating of overcurrent protective devices (OCPD) always needs to be equal to or lower than the ampacity of the protected conductor.
October 11, 2016 - CE Code Section 10 “Grounding and bonding” talks of bonding metallic systems together to the grounding conductor. This reduces the danger of electric shock and property damage by providing a low impedance path for fault current back to the source, and establishes an equipotential plane, such that the possibility of a potential difference between metal parts is minimized.
Light + Building 2018
March 18-23, 2018
IEEE Electrical Safety Workshop (ESW) 2018
March 20-23, 2018
Electrical Safety Innovation Summit 2018 • Montreal
April 12, 2018