RECALL – Nexans AC90 12-gauge cable due to fire hazard
September 15, 2021 | By Anthony Capkun
September 15, 2021 – Health Canada advises of a recall involving Nexans 4C12(1) AC90 12-gauge electrical cable.
The recalled product contains 14-ga electrical conductors in the cable rather than 12-ga (as labelled). Running a current suitable for a 12-ga conductor through a 14-ga conductor may cause overheating, posing a fire hazard.
The recall involves Nexans 14-ga electrical cable labelled as
4C12(1) AC90 CU ST1 ZERO HAL
and sold in 75-metre spools.
The product can be identified by product number 633735 and UPC 62208933735.
This product was available to electrical contractors who may have used the cable in Canadian buildings.
As of May 5, 2021, the company has received no reports of incidents or injuries in Canada. At the time, the company reported that 81 units of the affected product were sold in Canada from October 2020 to January 2021.
The units were manufactured in Canada by Nexans Canada Inc. and distributed by various electrical distributors.
For more information, contact Nexans Canada Inc. at 800-268-9473 or email@example.com.
N.B. The Canada Consumer Product Safety Act prohibits recalled products from being redistributed, sold or even given away in Canada.
Print this page